New farming facility for research on and breeding of lumpfishNamdal Rensefisk AS has entered into an agreement with AKVA group and Plastsveis to build a fish farming facility for research on and breeding of lumpfish.
The facility is based on flow-through rather than recycling. Thus filtering and treatment using UV in addition to heating is not particularly important. The facility will be supplied with an intake system with pumping, filtering and aerating of seawater, where the water is then distributed to the existing section and to the new facility. It will be supplied with a fine filtration system with a drum filter and UV for water destined for the fish in the research facility. The energy plant will ensure adjustment of the temperature to different zones, and for some tanks there will be individual temperature control up to 12 degrees. A tank system will be supplied for lumpfish from egg to adult fish, with outlet water filtering and outlet water system.
What distinguishes this facility from other facilities, and from the remainder of the fish farming facility at Namdal Rensefisk, is the filtering ratio and temperature management. Aqua Gen and Namdal Rensefisk have stringent requirements to filtering and temperature control, which greatly impact the facility's complexity. Instead of placing a single ring pipe under all of the tanks and basic outlet water pipes from the tanks and into the sea, we will have to manage both intake and outlet water separately to numerous zones and individual tanks. Filtering requires many extra filters that are both expensive and that require a great deal of infrastructure in the shape of pipes, valves, sensors, control electronics, etc.
The energy plant comprises a heat pump and exchange system that has to be flexible in order to achieve individual temperatures in different zones and tanks. Another aspect of the energy plant is that the heat from the outlet water should be recycled, and this means that the outlet water must be treated and pumped through heat exchangers before being returned to the sea. In order to supply even pressure and total gas saturation in the water, the water must be supplied from dedicated level tanks at the final stage of the intake system (seawater intake, filtering, energy, aerating).
“We have worked on this contract since the autumn of 2016, and it's very satisfying to have come so far in the process that the plans will become reality. It's interesting to follow the customer in this exciting project, and we will do everything in our power to earn the confidence,” says Sten Roald Lorentzen.
The progress plan is not yet finalized, but a construction time of approx. 10 months is estimated. Around 9,000 hours will be used to install the facility, in addition to 5,000 hours for production at Berg.Espalda